Here, we'll show you how to install an electric strike to a door controller.
Strike Installation Overview
When installing an electric strike, we recommend using an 18/2 shielded wire. Pull the 18/2 shielded wire through the opening of the enclosure. Make sure the ends are stripped and prepped for installation. In this article, we will be cutting negative. (We use the second reader port, as shown in the image.)
1. Remove the second reader port (labeled + - 0 1 L) terminal block (The first or primary reader port terminal block may also be used.) Insert the red wire into the positive output. Replace the terminal block.
2. Remove the NC C NO terminal block. For Fail-safe configuration, insert the black wire into normally closed (NC). Replace the terminal block.
For Fail-secure configuration, insert the black wire into the normally open (NO). Replace the terminal block.
3. Install a jumper over the pins next to the main relay. Because we are cutting negative, place the jumper on the top two pins. This will force a negative polarity out of the main relay.
When using a strike, you will need to make sure a diode is installed. Install the diode at the strike with the striped end on positive and the black end on negative.
The installation of an electric strike is now complete.
Should you require any technical assistance, please contact our knowledgeable ProdataKey Support staff. Your support queries covering hardware, software installation, trouble tickets, troubleshooting, return merchandise authorization (RMA), or any other questions will be addressed as immediately as possible.
Phone: 801.317.8802 option #2 or direct at: 801.206.4086 and 801.871.3009
- Direct Dealer Support Line: 801.206.4086
ProdataKey, LLC - 67 West 13490 South, Draper, Utah 84020 United States