To wire an alarm panel to pdk as a dry contact, run the closure wires from the alarm panel into one of the following: either the A port (for DPS) or the B port (for REX). If it is run to the A port, then it will be necessary to create a rule. Run the other wire into the negative (-).
For a fire alarm: on DPS (for A) or on REX (for B) close, then force open all doors.
If doing output to an alarm panel then you can use the relay that is triggering the lock. To do that, you must have the alarm panel set to ignore all closures after the first one. You would then run it the same way your locks were set up unless it is powered. If it is powered, then run it into an auxiliary (AUX) relay.
Should you require any technical assistance, please contact our knowledgeable ProdataKey Support staff. Your support queries regarding hardware, software installation, trouble tickets, troubleshooting, return merchandise authorization (RMA), or any other questions will be addressed as immediately as possible.
Phone: 801.317.8802 option #2 or direct at: 801.206.4086 and 801.871.3009
Direct Dealer Support Line: 801.206.4086
ProdataKey, LLC - 67 West 13490 South, Draper, Utah 84020 United States